LPG id connected in a manifold does not need a license.
The shed in which the manifold is kept should have LPG leak detector, should be well ventilated, should have Fire Hydrant Line with monitor and Water Sprinklers.
The cylinders should be connected all the time to manifold.
Please check cylinder expiry months.
It is basically National Building code and the Fire Act
In Maharashtra, the Industries need permissions of constructions even for a temperory (Monsoon) shed from MIDC. (Maharashtra Industries Development Corporation)
Once the company applies the MIDC for construction commencemnt certificate, we have to take NOC from MIDC Fire Department.
They issue Provisional NOC, in which they specify the fire protection systems but these are based on the provisions given in National Building Code.
If you want copy of fire Act pl let me know I shall send on your personal id
The license to posses the LPG cylinders is covered under gas cylinder rules. Under this rule one have up to
100 kgs with out any license. There is no provision that cylinders connected in manifold does not need any license. NO Licenses for cylinders connected to mainfold is mentioned only in OSID guidelines which can not be treated as legal requirements.
for information please.
Refer LPG Industrial/Commercial Installation ISI code of Practice BS 6044 part 1.
The installed capacity of a LPG Manifold Installation should not cross 1000kg of LPG. If it is crossing split it. Means have two chambers of LPG Manifolds separately, comprising following quantity of cylinders in one manifold. The two rooms should be separated by brick wall.
1) 19 kg capacity cylinders = 52 cylinders on one manifold (room)
2) 35 kg capacity cylinders = 28 cylinders in one room
3) And if 47.5 kg capacity cyls = 21 cylinders in one room.
No loose cylinders should be kept. All the cylinders should be connected. etc etc etc... refer 6044 part 1 & 2
If it is going to cross 1000kg "Explosive License" is required alongwith local approvals.
For this reason you reduce the manifold size by having LoT (Liquid Off-Take) Manifolds with LP Gas Vaporiser.
Any info help post your email. Thanks n Regards.
100kg (means 6 cylinders maximum in terms of quantity of cylinders -Domestic 14.2kg capacity) one can keep at one location unconnected though cylinders are properly sealed and fitted with Derlin Cap put on those. This rule is meant for LPGas Distributors and not to anybody else. It means when it exceeds 100kg it needs Licence to store or to keep collectovely. Other than LPGas distributors one family cannot be in possession of more than 2 domestic cylinders (one connected to stove and another in store as additional). LpGas Distributors normally keep not more than 6 cylinders (filled) at their shop for quick/emergency supply for which license is not needed as they have licensed godown. Other than LPGas Distributors one cannot be in possession of LPGas cylinder (even ONE of any capacity -5 kg to 47.5kg) without proper document called SV.
As far as Mr HRK's case is concerned if installed capacity of Manifold is exceeding 1000kg it needs Licence to be issued by The Chief Controller of Explosives, Nagpur. You have to have adequate size of Manifold Location with fencing and open space all arround the Installation. The rule book is too big. Hence go for LoT Manifold Installtion which comprises less number of cylinders in one manifold.
Cylinder rules is under Petrolium act
The other is explosives act
They are both applicable, not in alternate.
The cylinder rules say "possession". Nothing there says its for LPG distributors only. Anyone having LPG cylinders in their possession, irrespective of whether it's connected or stored, will have to follow the rules.
Further, wee are talking of commercial gas cylinders in a factory, not domestic cylinders in a home.
Distributor is authorised to have possession and can store at licensed premises. Others can have or in possession of legal way procured cylinder. either domestic or industrial. But with no valid document one cannot have or in possession of one single cylinder filled or empty. I hope this is clear.
Now industrial/commercial cylinders are available in 5kg, 19kg, 35kg and 47.5kg packages (capacity). I am putting both domestic and industrial aspects of rule and act of LPG Code of Practice. For all others (other than gas distributors) possession of cylinders is by way of valid document. And such legally obtained cylinders in industrial case cannot be unconnected or loosely stored. These cylinders(empty or filled) should be connected to the user line or manifold. I think it is clear.
The point in OP was about whether he can have 1000 kg in LPG gas cylinders in a manifold. The ISI / BIS rule and norm for setting up manifold is one aspect. There is also another aspect that is covered under Explosive Act and Petroleum Act that needs to be adhered to.
I would like to know what are the statutory approvals one should have for accepting such a system. Though the quantity of gas is large, Inspectorate of Explosives are refusing to issue any certificate.
How do we accept such a system which has flouted many rules ? I am told that the major oil company's certificate is enough who has done the installation and will supply the gas.
Are there any private parties who can do Hazop and safety audit and issue the certificate ?
Any guidelines ?
If Installed capacity doesn't exceed 1000kg then LICENSE from Explosive Department is not required. However you need to have in possession of PRESSURE & LEAK TEST REPORT with Drawing details layout duly signed to be furnished by the contractor who has carried out the installation. This is very essential. Have proper ventilation at the bottom and at top of the manifold/storage room. No electric switches or lamps/bulbs to be used in the cylinder premises. You can use concealed bulbs approved by the authority (the contractor knows this) with the switch placed in the other location. As far as possible please avoid this. No mobile phones to be used in the manifold room. No smoking too. Get replaced the empty cylinders with filled ones by the authorized delivery boy.
Dear Mr Srini
Pl give couple of days to solve your query.
Thanks & Warm Regards
I have a question this is the MAJOR mistake ever did in INDIA when you given a contract to CONTRACTORS you should provide SOW to contractors prior to BID in that SOW should includes which standards they should follow, They must need to provide as build drawing, test certificates, warranty certificates etc..,, As you mentioned which has many design faults and no references to the Gas safety rules or IS 6044. . . its 100% purely your fault. . . Never give a chance to contractors or subcontractors to speak as a customer we need to say what we need. . .
We are not pro-active on your case what ever we said to sub contractor they do the same we are failed to direct them rightly. . .
If go by NFPA 70: NATIONAL ELECTRICAL CODE May you will get all electrical standard requirements of gas storage area.
Then Mr.Abhinandhan highlight one good point regarding Mobile phone usage in manifold room. You can place sign boards whatever it is you can’t control they can used the phone in this case better you can install ‘’cell Phone Jammer ‘’ cell Phone mobile Jammer transmits low power radio signals to cut-off communications between cell phone and cellular base-stations.
What I suggest in this case better to contact any good consultant make sure you did it right because in an apartment complex of more than 1000 apartments if something went wrong it will become a disaster.
Prevention is better than cure. . .
Thanks for your input Mr.Abhinandhan. . .
Keep on Sharing. . .
I would like to add some more critical points in the safety of the LPG manifold (LOT):
- In case more than 1000 Kgs of LPG isntallation is there, then number of installtions should not be more than 4 (including stand by).
- Minimum of 3 meters distance from all sides shaould be avaialble in between the two installations.
- Vapourizer (other than Direct Heating) should be atleast 2 meters away from the LPG manifolds.
- Only Flameprrof (INtrinsically safe) electrical fittings should be insatlled.
Wholesales 4G Cell Phone Jammer - 4G Jammer - LoJack Jammer